Why coordinate with many fire safety contractors when you can work with just one? Northwest Fire Systems is a Level III Fire Protection Contractor serving the Auburn, WA area with comprehensive fire protection services.
Our goal is to provide the best value with the best customer service from the best people in the business. And, as you can see from reading our Auburn, WA reviews, we meet our goals!
for Auburn, WA
Our Reviews by City
Great Service, Very Thorough, and Friendly Staff
Shardannay - Auburn, WA
Thank you Marc for stopping by to say hello! We appreciate your service.
Jan - Auburn, WA
Robin - Auburn, WA
She is the best and so helpful,
Mike - Auburn, WA
Robin - Auburn, WA
Amazing team and great service!
Keri - Auburn, WA
Neil - Auburn, WA
fast friendly servicre
Excellent Company To Work With
Diane - Auburn, WA
I can't express enough how NW Fire Systems are experts at their job, and so excellent to work with. They truly take care of their customers in every way. Thank you!
Greg - Auburn, WA
Jesse is a class act.
Terry - Auburn, WA
I appreciated the professionalism from Larry the tech.
Annual Fire Alarm, Backflow, Sprinkler and Fire Extinguisher Inspection
Fire Alarm Repair - Instant Repair Silent Knight 5700 FA-1 / Need Infor: On site Instant Repair - (3) 12v 8ah battery replacements
Deficiency Repairs 3 year dry sprinkler full trip test
Monthly Fire Pump Inspection.
Monthly Fire Pump Inspection
Annual Fire Extinguisher Inspection of Two Missed Extinguishers
Annual Sprinkler Inspection
Deficiency Repairs Watts 007M1QT 151359 BFP-18 Next Meter left side Bldg. 3: Backflow failed testing. #1 Check valve assembly failed - Recommend replacement of #1 check valve assembly. 2" Watts 007M1QT Serial #151359 Located next to meter in front of Bldg. C (6260) This is a domestic backflow for Bldg. C so water will need to be shut off to the building for 2-3 hours. Watts 007M1QT 150876 BFP-17 Next to meter right side Bldg. 2: Backflow failed testing. #1 & #2 check valve assemblies failed - Recommend replacement of #1 & #2 check valve assemblies. 2" Watts 007M1QT Serial #150876 Located next to meter in front of Bldg. C (6260) This is a domestic backflow - I believe it feeds Bldg. B so water will need to be shut off to building for 2-3 hours. Watts 007M1QT 151222 BFP-23 Next to meter Bldg 10: Backflow failed testing. #2 check valve assembly failed testing and #1 check valve is close to failing - Recommend replacement #1 & #2 check valve assemblies. 2" Watts 007M1QT Serial #151222 L
Semi-annual Clean Agent Suppression System Inspection
Annual Fire Extinguisher Inspection
Annual Sprinkler, Fire Alarm, Backflow, and Fire Extinguisher Inspection
Semiannual clean agent inspection