There’s no better way to ensure Kirkland, WA your property’s complete fire safety than with a call to Northwest Fire Systems. We meet all your fire protection needs with system installation, inspection, maintenance and more.
Why coordinate with many contractors when you can work with just one? See how we stack up against the competition by reading our reviews today.
for Kirkland, WA
Our Reviews by City
Marlon is Great, friendly and know his thing
Judaveyn - Kirkland, WA
the service is Great,from Kathy to the service crew to materials procurement and the installation are awesome. project got done in time.
Jeni - Kirkland, WA
Campbell - Kirkland, WA
David - Kirkland, WA
He was very knowledgable and walked me through what I need to know
Fast, Efficient and Friendly
Dennis - Kirkland, WA
Working with NW Fire is always effortless and enjoyable. The techs know their stuff and are courteous and professional
Efficient and Effective!
Regina - Kirkland, WA
Allec was out to our community in Kirkland today and was so helpful in testing our backflow and was nice enough to provide details to the city on our behalf. He was thoughtful to tell me that our fire extinguishers need servicing as well so it's nice to have vendors that care and do the job right the first time!
Annual Sprinkler Inspection
Fire Alarm Service Call
Brian FA service 2 hours Replaced 5 x 12v 8ah batteries Trouble on panel is a open circuit in NAC output #1 , the panel has 4 nac outputs. Notice was not given to building occupants so I was not able to test which horns and strobes are on the open circuit. Fastest way to trouble shoot is to trigger all horns and strobes to see which are not working so we can locate the break in the circuit. Also horns and strobes would need to be tested to verify they are working after open circuit is repaired. I was informed sounding horns was not possible today. For trouble shooting and repair of open circuit give all occupants proper notice
7/22 - Annual Sprinkler, Fire Alarm, and Fire Extinguisher Inspection
Found AC transformer unplugged and AC loss troubles on panel. Plugged in transformer, reset AES and FACP both show normal and troubles cleared. Monitoring station is receiving signals
All batteries replaced. We did not have proper notification sent to units to replace horns. Client will reschedule
Replaced relay module for elevator zone 40 . Customer had parts on site and those were used. We were unable to locate the second annunciator that was in trouble. Client will research where the annunciator is and follow up.
Backflow service call