Fire Safety You Can Trust In Monroe WA
Since 2008, Northwest Fire Systems has been providing the ultimate in fire protection services to the people of Monroe, WA and the surrounding areas. When it comes to fire safety, they are second to none.
Read below to find out what your neighbors in Monroe, WA have to say about our service, then call us to ensure your home or business is protected!
for Monroe, WA
Our Reviews by City
Deficiency Repairs Wilkins 975XL 137001 BFP-5 / Laundry Room Behind Washers: Backflow failed testing. Relief failed to vent - recommend full rebuild kit. 3/4" Wilkins 975 Serial #137001 Located in laundry room behind washers. Wilkins 975XL W261859 BFP-6 / Laundry Room Behind Washers: Backflow failed testing. Check 2 leaked by - recommend full rebuild kit. 3/4" Wilkins 975XL Serial #W261859 located in laundry room behind washers. 11: Fire Extinguisher due for service. (1) 5lb FEX due for 6 year service.
Annual Fire Alarm, Sprinkler, Backflow inspections Deficiency for Wet SPK-1 / New Customer: 5 year is due 1 water gauge Check at riser IPE (12-15 ft ladder)
5 year maintenance of Wet system IPE, FDC Back Flush and Gauge replacement.