Northwest Fire Systems provides complete fire protection services to commercial clients in Puyallup, WA and the surrounding areas since 2008. From installing fire alarm and sprinkler systems to completing scheduled testing and maintenance, we make sure your property is safe from fire.
We have the best people and customer service, and provide the best value for your money. Read our reviews to see why Northwest Fire Systems is THE fire protection leader in Puyallup, WA.
for Puyallup, WA
Our Reviews by City
Wenses - Puyallup, WA
Good customer relation ship.
Wayne - Puyallup, WA
great at letting us know what was done
Jake - Puyallup, WA
I believe the tech's name was Marlow. Marlow was in and out quick and clean it seemed like. He helped me call to put the system in test and take it out as I did not know how, because I am a new hire. He was also friendly with my co-workers. I hope to see Marlow again.
Cameron - Puyallup, WA
On time/well planed/all around coverage/efficient work and knowledge.
Wenses - Puyallup, WA
give a summery or explain the work you have done or service on site before you sign off for the day to who ever in-charge of your customer.
Deficiency Repairs Silent Knight 5207 FA-1 /: Fire alarm batteries are due for replacement. 2 x 12v 8ah batteries Watts 007DC Unreadable BFP-1 / Vault Near FDC: Unable to test domestic backflow during annual inspection. Backflow is located in vault - Vault needs to be pumped out and backflow tested. Dry SPK-1 / Laundry Room Bottom Floor: 4” Grinnell F3021 face plate gasket is leaking - Recommend replacement of face plate gasket. Dry SPK-1 / Laundry Room Bottom Floor: Grinnell F3021 Valve did not trip under 60 seconds - Will need an accelerator installed. Note: the drain is piped up, and there is no drain for the ITV upstairs to empty. Will need hose bib and 50' foot hose. Febco 806YD B589 BFP-4 / Riser Room: Backflow failed testing. #1 check valve failed - Recommend replacement of #1 check valve assembly. 4" Febco 806YD Serial #B589 Located in fire sprinkler riser room. Febco 805Y W1570 BFP-5 / Riser Room: Backflow failed testing. #1 & #2 check valves failed - Recommend replacement
Replaced all batteries
Annual FA inspection
Annual Fire Alarm, Sprinkler, Backflow, and Fire Extinguisher Inspection
Annual fire alarm inspection not complete. Wenses Fernando requests to reschedule for horn and strobe testing as well as units that were not accessible today. Added pictures of units that were tested today Sprinkler inspection was completed today.
Fire Alarm Diagnosis
Annual Sprinkler, Standpipe, Fire Alarm, Backflow, and Fire Extinguisher Inspection
Tested and confirmed duct smoke operation and shutdown of air handler units. Dampers did not change state upon activation or deactivation of air handler units . Hvac company should be called to check damper operation
Deficiency Repairs Wilkins 375ADA X18278 BFP-3 Hot box on Eastside: Backflow failed testing. Relief failed needs replaced. Wilkins 375A 4” Serial #X18278 Backflow Repair