Northwest Fire Systems Works To Meet Your Fire Protection Needs
Northwest Fire Systems provides commercial clients with complete fire protection in Kent, WA. Ensure your people and property are protected during a fire emergency by scheduling with us today.
We offer fire extinguisher inspections, fire alarm system installation and testing, as well as many other fire protection services. Check out our full list of fire protection products and services to see how we can meet your needs.
Northwest Fire Systems is family owned and operated and can fulfill all of your fire protection needs while planning around your specific space and function requirements. Read our customer reviews to see examples of our quality service in the Kent area.
for Kent, WA
Our Reviews by City
Mike - Kent, WA
very professional and was on time
Clyde - Kent, WA
Quick and effectient
Very prompt and friendly staff
MFG'er in Kent - Kent, WA
Awsome service and communications
Gary - Kent, WA
Small job, but I felt just as important as a customer on a large job.
Cynthia - Kent, WA
knowledgable, respectful, easy to work with
Chris - Kent, WA
Kara - Kent, WA
The service was quick and staff were very knowledgeable and friendly.
Gary - Kent, WA
Jesse explained everything, very knowlegable.
Fast reliable Services!
Alyssa - Kent, WA
Rick - Kent, WA
The tech did a good job. Made sure all extinguishers were inspected.
Deficiency Repairs Repaired and retested fire main ad bypass backflow preventers Scoped fdc and added 4 locking Knox caps
Annual Fire Alarm, Sprinkler, and Fire Extinguisher Inspection
Annual Fire Alarm & Sprinkler Inspection
Fire Alarm/BF repair
Fire Extinguisher Quote Installed 10 new fire extinguisher box covers Installed 10 new 5 lbs abc fire extinguishers Swapped 13 fire extinguishers for 6 year service Swapped 14 fire extinguishers for 12 year service
Annual fire alarm inspection
Annual Sprinkler and Fire Extinguisher Inspection
Replacement for (2) hydro and (1) 6 year fire extinguishers parts only completed while onsite for annual
Deficiency for Wet SPK-1: FDC cap missing. Replace cap and flush or scope FDC (in vault by piv) Deficiency for Febco Can't read Can't read BFP-2 / Fire Vault: Fire main Backflow - make and model unreadable Needs a breakaway lock for valve chain Check #2 failed . Replace entire check 2 assembly and order new bolt kit as bolts are rusted and corroded. TC# 3 and 4 have the handles corroded and are unusable and need to be replaced Vault will need to be pumped out Deficiency for Febco Can't read Can't read BFP-3 / Fire Vault: Fire bypass Backflow failed - make and model unreadable Both shut off #1 and 2 have handled rusted and Corroded and won’t close. Needs new shutoff handles or entire shutoff valves. Vault will need to be pumped out Annual Sprinkler and Backflow Inspection