Northwest Fire Systems Works To Meet Your Fire Protection Needs
Northwest Fire Systems provides commercial clients with complete fire protection in Kent, WA. Ensure your people and property are protected during a fire emergency by scheduling with us today.
We offer fire extinguisher inspections, fire alarm system installation and testing, as well as many other fire protection services. Check out our full list of fire protection products and services to see how we can meet your needs.
Northwest Fire Systems is family owned and operated and can fulfill all of your fire protection needs while planning around your specific space and function requirements. Read our customer reviews to see examples of our quality service in the Kent area.
for Kent, WA
Our Reviews by City
Mike - Kent, WA
very professional and was on time
Clyde - Kent, WA
Quick and effectient
Very prompt and friendly staff
MFG'er in Kent - Kent, WA
Awsome service and communications
Gary - Kent, WA
Small job, but I felt just as important as a customer on a large job.
Cynthia - Kent, WA
knowledgable, respectful, easy to work with
Chris - Kent, WA
Kara - Kent, WA
The service was quick and staff were very knowledgeable and friendly.
Gary - Kent, WA
Jesse explained everything, very knowlegable.
Fast reliable Services!
Alyssa - Kent, WA
Rick - Kent, WA
The tech did a good job. Made sure all extinguishers were inspected.
Fire Extinguisher Quote Installed 10 new fire extinguisher box covers Installed 10 new 5 lbs abc fire extinguishers Swapped 13 fire extinguishers for 6 year service Swapped 14 fire extinguishers for 12 year service
Annual fire alarm inspection
Annual Sprinkler and Fire Extinguisher Inspection
Replacement for (2) hydro and (1) 6 year fire extinguishers parts only completed while onsite for annual
Deficiency for Wet SPK-1: FDC cap missing. Replace cap and flush or scope FDC (in vault by piv) Deficiency for Febco Can't read Can't read BFP-2 / Fire Vault: Fire main Backflow - make and model unreadable Needs a breakaway lock for valve chain Check #2 failed . Replace entire check 2 assembly and order new bolt kit as bolts are rusted and corroded. TC# 3 and 4 have the handles corroded and are unusable and need to be replaced Vault will need to be pumped out Deficiency for Febco Can't read Can't read BFP-3 / Fire Vault: Fire bypass Backflow failed - make and model unreadable Both shut off #1 and 2 have handled rusted and Corroded and won’t close. Needs new shutoff handles or entire shutoff valves. Vault will need to be pumped out Annual Sprinkler and Backflow Inspection
Annual Fire Alarm, Backflow, T&M No Contract Watts LF009M2QT 067594 BFP-1 / N Bay Wall: Annual BFP Inspection - T&M No Contract Silent Knight 5808 FA-1 / Garage: Annual Fire Alarm Inspection - T&M No Contract
Evacuation map shows a pull station located at the north west exit door in the PAT room. There is no pull station in that location so it does not match the evacuation plan map. Per NFPA 101 only one pull station is required per system. It is ultimately up to the AHJ if they will require one to be installed . I have documented my findings and we will help in contacting the local fire department for their opinions or requirements. After the local fire department makes their statement. Forward their decision to CBRE and insurance company. And they can make the final decision to either add a pull station in area in question if the fire department says it’s not necessary. Or update the evacuation plan map. Main facp is located on the east side of the building across the parking lot in a different tenants space. I did not see the main facp for myself as notice will need to be given to tenant. The pull stations installed at other exits are edwards see attachment for part number. Recommend ed
Annual Fire Extinguisher Inspection
Annual Wet Sprinkler & Antifreeze System Inspection
Annual sprinkler, backflow and fire extinguisher inspections -